Service Call - Diagnostics 2015
Gas PRV Problem - A large new project had issues with gas boilers and package AHUs shutting off due to erratic gas pressure. Incoming pressure was steady at 2 in. WC, while downstream pressure fluctuated from 0 to 12 in. MSC technicians found that the installed pressure reducing valve was unsuitable for the system and successfully replaced it with the correct PRV.
About MSC - The Go To Guys
We are a service subspecialist in the technical intricacies of HVAC, process cooling, and building automation systems in commercial, industrial, and institutional environments. MSC is recognized as the leading industry expert in solving elusive problems and attaining peak performance from clients’ mechanical equipment and overall systems.
Located in northern New Jersey, MSC is the only specialized contractor of our kind in the Northeast and Mid-Atlantic regions. We are MSCA STAR-qualified, NEBB-certified, fully-licensed in electrical, plumbing and HVAC, and our engineers and technicians are the most knowledgeable in our field.
Mechanical Service Corp.
41 South Jefferson Road
Whippany, NJ 07981